NEMA 4X indoor/outdoor use
Welded Type 304 Stainless steel construction
3/4” thick foam core insulation
Laminated poly/aluminum facers
Dimensions: 36”h x 24”w x 32”d
Weight: approx. 200 lbs.
Two doors (front and rear), each fully gasketed, hinged left, latched right
Standard 1/4 turn latches, top right latch per door, “barrel style” and padlockable (padlock not included)
Grounding studs (4) on doors and inside enclosure
Side flange style with punched (not tapped) holes, for use with “clip-nuts” (included).
Approx. 32” high and horizontally-adjustable (front to-rear) on uni-strut.
Cable Exit Plate
Type 304 stainless steel
Dimensions:5.5”h x 13.5”w
Gasket covering 2”h x 12”w cable exit cut-out, plate
4 built into enclosure (two on right, two on left)
Air Conditioners- 2 included
Thermoelectric solid state
Built-in adjustable thermostat
Stainless steel covers
Stainless steel mounting flange (20-1/4”h x 13”w)
Neoprene mounting gaskets
Stainless steel mounting fasteners
Certification to UL/CSA standards
One condensate drip pan per cooler
Drip pan fittings and length of flexible PVC drain tubing plumbed with enclosure.
Small drain holes on right and left sides of enclosure (towards bottom).
Air Conditioner Requirement:
(qty2) 1500 BTU/HR rating (each). Optional upgrade to 2500 BTU available for purchase.
NEMA 4X configuration
220 VAC (4.6 amps) (or, specify 110V instead of 220V at time of ordering)
Air Conditioner Dimensions
Through-mount design, will protrude 3-5/8” into enclosure.
External Air Maximum Ambient Temperature
The ENC36-B-1500 has performed in ambient air temperatures up to 95-100ºF. The ENC36-B-2500 is expected to perform properly in temperatures up to 110ºF however company has not yet recorded upper performance value under those conditions so this value is an estimate only. Note that exposure to direct sunlight or radiant heat from a nearby object, blockage of vents, dirt buildup and aging may also impact system performance in high temperature conditions.
†Exposure to direct sunlight or radiant heat from nearby objects can act as another heat input to enclosure and therefore should be avoided, especially in warm climates. Use of a well-ventilated solar shade is recommended if placed outdoors and without blockage to the air conditioner vents. Also direct exposure to sea spray should be avoided as this may shorten the service life of the enclosure.
††Specifications and appearance are given as guidelines and may change without notice.